9000 substation integrated automation system
The 9000 integrated substation automation is the background monitoring system of substation integrated automation based on the computer, using the international standard, multi-window and multi-task system, running on the Chinese windows nt or Windows 98 above operating system environment, stable operation, high reliability, simple operation and easy to learn.The system select with the industrial control machine of high performance, high reliability , the average failure free operation time is more than 25 thousand hours, the software modularization design, real-time database and flexible configuration, greatly improve the reliability of the system.
１）Data acquisition and processing
Collect the substation information to the Real-time operation by CDT , including conventional RTU information and protection information.
The collective information have:
ａ. Analog quantity includes Frequency, voltage, current, active power, reactive power, temperature, etc.
ｂ. quantity of state includes switch, knife gate, the total accident signal, protection signal, transformer tap position,etc
ｃ. Pulse electrical measurement
ｄ. sequence of events recording, SOE
ｅ. Measurement and fixed value that sent out by protection relay
ｆ. Fault action information sent by protection device
ｇ. Self diagnosis information transmitted by protection device
ｈ. Protection device send the trip report, trip waveform etc.
ａ. Remote signal processing
ｂ. reasonableness check
ｃ. Electric quantity treatment
ｄ.Event sequence record processing
ｅ. Protection information processing
２）Calculation of the amount of processing and special operation
Provide the following standard calculation for the user to choose to use
ａ.According to the active power, reactive power, voltage, current of which three known amount, and another unknown quantity and power factor
ｂ. Analog library, library statistics, cumulative storage add, subtract, multiply and divide calculation
Generation of road handle：When the circuit is on the bypass route, the active power, reactive power and current equivalent of the bypass will be replaced by the bypass.
Statistical specified value：Early peak, evening peak, early Valley, late Valley, daily maximum, daily minimum, etc.
The number of adjustment times of the main transformer, the capacitor set time, the number of investment, the investment rate and the time of the peak input.
Monitoring of remote measurement
a. The measurement and calculation of the system is carried out in the system.
b. Take the time delay and the dead zone to prevent the running of the value in the vicinity of the limit and frequent alarm
c. Cumulative failure time and number of times, for the calculation of the pass rate
d. Abnormal occurrence and recovery when the alarm processing
（ⅰ）Condition record sheet
（ⅱ）Remote signal change record
（ⅲ）Remote information record
（ⅳ）Event sequence record
（ⅴ）Protective action record
（ⅵ）Protection of self diagnostic information record
b. Alarm source definition
（ⅰ）Change of remote signal state
（ⅱ）Telemetry value anomaly
（ⅲ）Tele-control equipment status change
（ⅳ）Communication failure with the total control device
c. Alarm selection
（ⅱ）Flash and automatic stop flashing display
（ⅳ）Automatic push screen
（ⅴ）Record and file the log in status
（ⅵ）Log in remote record form, and file
（ⅶ）Log in telemetry exception record form, and file
（ⅷ）Cause accident recall
Accident recall, recall
Record the accident before the M frame, after the SCADA frame of the N data of all content and the process of the accident, M and N by the user to customize, users can also choose to the feature.
Graphic element editing function
Has a rich variety of graphics, mainly to complete the various types of screen generation, modify
Graphic display operation
The graphical display of high resolution, multi window technique, the application of the operation, in response to the application of the message returned in response to the requirements of the application.
（ⅰ）Provide the TAB package, for the user to generate a variety of data reports
（ⅱ）Print timing、Summon print
The 9000 Content of substation integrated automation system：
1.9000 Engineering management of monitoring and control system：
9000 Engineering document organization, the 9000Engineering Development Organization, 9000 engineering backup, 9000 Online maintenance,9000 Engineering document reference.
2.Real time database and variable point definition:
The 9000 General principles of real time database organization in substation automation system,9000 the definition of loop ,the 9000 Variable and variable attributes.the 9000 Definition and reference of variable point, 9000Attribute modification of variable points in substation integrated automation system, 9000Common techniques for real time database definition、 9000 Assignment of variable points.
3.Mapping tools and animation:
9000Overview of window screen, 9000Picture element, 9000Common picture organization tool,9000,Animation connection, 9000 Window controls,Common window mapping techniques.
4.Background language and system function:
9000 Use of background language,9000 The use of system function
5.9000Network node configuration of substation integrated automation system:
Classification of 9000 network nodes、 9000 Node composition、Picture organization、9000Communication between network nodes、 9000 Parameter configuration of network nodes、 9000Dual network fault tolerance of substation integrated automation system
6.9000Alarm and alarm processing:
9000 Alarm classification、 9000 Alarm processing、Remote signal to alarm and its configuration、SOE Alarm and configuration、Switch action alarm and its configuration、Alarm confirmation、Configuration method of alarm push picture、Sound alarm and its configuration、Alarm limit management
7.9000 Remote / remote control operation and its configuration:
9000 General process of remote control / remote control、 9000Remote control and remote control / remote control of the local, remote control；Remote control / remote control interface and its calling method
8.9000 Remote setting and fixed value management:
9000 Set value model, set value of the call and set, set the value of the library management, fixed value management interface and its call method
9. The freezing process of electric energy broadcasting and 9000 treatment:
Electrical measurement of the 9000, the conversion of electrical energy, electrical energy acquisition process, the history of the power of the database to save energy
10.9000 Remote signal processing and signal reset:
9000 the expression method of remote signal、Assignment method of 9000 soft remote point、 9000Total signal and signal processing method,9000 two point remote signal processing method、 9000 signal reset process
11.9000 Protocol driver and its configuration:
9000 data acquisition、Communication protocol and configuration of the concept 9000 supported by data forwarding and analog disk drive, and the development of communication protocol driver for 9000 substation automation system
12. 9000 timing control:
9000 batch control
13. 9000 real time database and real time information browsing:
9000 real time database, 9000 real-time database dump, 9000 real-time data tables, telemetry data query in real time, the electric energy data classification in real time, real-time query tele-signalling state data browsing, real-time trend curve data browsing, XY real-time curve data browsing, bar graph / pie chart real-time browsing
14. 9000 historical database and historical information browsing:
9000 organization of historical databases、 9000 historical data sheet、Historical data query and browsing、System operation record query SOE query、History of remote signal change query、History switch action query、Historical telemetry data query、Other historical inquiry
15. 9000 file database and user database management:
9000 the use of file database、9000 user database and 9000 interface、The background language implementation of accessing the user database
16. Report function:
9000 the use of system report function
17. 9000 management tools: the statute library management tools, 9000 user management tools, template library management method
Loop template library management, standard window management and reference method
18. 9000 gallery and gallery management tools:
9000 equipment library management system overview and function, using the method to explain the 9000 integrated automation system of substation equipment drawing management system; including system menu; system tools, methods of view gallery; method of making library
19. 9000 system tool instructions:
Path setup tool, system auto login tool, database maintenance tool
20. 9000 explain the use of controls:
General control of the specific use of the method, variable view control, data source report control combo box, list box control, form control
21. Use of Report Builder:
9000 substation automation system report generator of the specific use of the method.
Background monitoring system hardware configuration requirements：
1．Selection of display (color plane right angle)：
1）10 KV/ 6KV in substation protection and control device number less than 15, you can use 19 inch display
2）Select the number of at least 21 inch display protection substation substation and 10KV 35KV more than the following.
3）In addition to the provisions of the model design institute, our company will be in accordance with the conventional Samsung display, Taiwan Advantech IPC configuration.
2．Monitor host selection：
1）Above 160G hard disk
2）Memory not less than 1G
3）Main frequency is not less than 2.0G
4）Sound card, card, card, CD-ROM, floppy drive, keyboard, mouse and other accessories
3．The alarm speaker: the saunterer series
4．UPS: backup and online two kinds of; can not be less than 1h; 1KVA
6．Communication line：Shielded twisted pair
- why is the price of the Generator protection unit so expensive
- The photovoltaic power will become the main battleground in the elec
- Will the intelligent power station replace the conventional power st
- analysis the future development trend of the relay protection
- The importance of relay protection in electric power system
- Application of relay protection in life
- Principle of inverse power protection of generator
- The principle and effect of the auto reclosure
- The difference between over current protection and over load protect
- features of transformer differential protection
- Working principle of differential relay
- Working principle of over current relay
- Automatic synchronization device function,classification