9695 transformer differential protection relay
this device can be the most perfect high-capacity distribution transformer with the 9672 transformer protection measurement and control device (backup protection),the Economical and practical way is to choose the 972C Transformer integrated protection relay instead of the 9672 transformer protection measurement and control device and 9695 differential protection device If the main transformer differential protection is needed ,the 9692、9693(main transformer differential protection measurement and control device)can be your best choice.
differential current instantaneous trip protection
Proportional differential protection of two harmonic brake
CT line-break Locking ratio differential protection
CT line-break alarm.
Measurement and control function
IA、IB、IC；Ia、Ib、Ic；DIa、DIB、DIC is electricity quantity
Optical fiber communication;
Principle of the differential protection
The range of the differential protection：that is the range of the two sides or three sides that current mutual inductor contains,the fault that is out of the range do not work.therefore the fixed value need not to cooperate with the border component,and then is the current instantaneous trip protection of non time limit to protect the inter-phase fault,circle fault and the grounding fault in the outline of the transformer windings.
Pilot differential current instantaneously trip protection
Which in essence reflect the protection act quickly the two side current of the transformer ,when the interior transformer occurs serious fault or the external two side or three sides of the transformer or the CT occurs short circuit ,then act and trip quickly.
Protective action criterion：Icd >Isd
Icd is the actual differential current of the same phase CT of the two side
Isd is the differential instantaneous fixed current value
Any three of them meet the requirement thatIcd >Isd then the differential will work to trip all the switch of the main transformer.
The differential current in the actual function= Ih * cosφ1 + IL*ＫLｊｘ*cosφ2
ＫLｊｘ（Unbalanced coefficient of low pressure side）= Ie2h（Two rated current of high voltage side）/ Ie2l（Low voltage side two rated current）
cosφ1 is the actual angle of high pressure side；cosφ2is the The actual angle of the low pressure side.
ＫMｊｘ（unbalance factor of the medium pressure side）= Ie2h（Two rated current of high voltage side）/ Ie2m（Two rated current of medium voltage side）
cosφ1 is the Actual angle of high pressure side；cosφ2 is the The actual angle of the medium pressure side.
The imbalance coefficient of high pressure side was 1
Proportional differential protection of two harmonic brake（with the function of the CT line-break locking）
The protection adopts the split phase type,that is any one of the Ａ、Ｂ、Ｃ Protection actions are outputed，The following criteria are all based on one phase.
Rate differential element protection act when the following types are set up at the same time:
among：Ｉh、Ｉl respectively is the High, low voltage side current Ｉsd is the Differential setting value of the instantaneous trip current;Ｉcdqd is the Differential protection door Kanding value;
Ｉzd is the stalling current,the main transformer value of the second circle average value of both sides of the current；and the third value is maximum value of a fault entry; is theTwo harmonic component of differential current Ｉcd is the fundamental component of differential current; Ｋ2 is the Two harmonic braking coefficient;
1) Differential protection of ratio braking
998 Transformer differential protection device using the conventional ratio differential protection, the use of the principle of the two harmonic brake, reliably avoid the differential circuit in the differential current and the effect of the inrush current.Its motion equation is as follows:
Icd＞Icdqd Icd＞K1*Izd （the or gate between them）
among：Icd is the differential current，Izd is the brake current,K1is the Ratio braking coefficient ,Icdqd Differential current threshold value
For double coil transformer：Icd＝| Ih＋IL | Izd＝| Ih一IL |／2
Simple calculation in debugging:
If the proportional differential act,then the Icd＝| Ih＋IL | > Icdqd；
Also meet with the demand of ：Icd＝| Ih＋IL | > K1*Izd = K1* | Ih一IL |／2
On the formula is to take into account the vector calculation, if only the calculation of numerical value, assuming high, low voltage side phase just a difference of 180 degrees;
The upper inequality is：Icd＝| Ih - IL | > Icdqd；
Icd＝| Ih - IL | > K1*Izd = K1* | Ih + IL |／2
Mode 1：if Ih > IL ；
Then ：Ih > IL +Ｉcdqd；Ih > IL*（2+ K1）/（2- K1）Ratio differential act
Mode 2：ifIh < IL ；
then：IL > Ih +Ｉcdqd；IL > Ih*（2+ K1）/（2- K1）
2) Proportional differential protection of two harmonic brake
In order to escape the magnetizing inrush current of the transformer in the closing moments, the device using second harmonic as magnetizing inrush blocking criterion, the movement equations for: ＜Ｋ2×Ｉcd
among is the two harmonics of A, B, C three phase differential current,IIcd is the corresponding three phase differential current，K2 is the two harmonic braking coefficient.As long as there is any phase to meet the above conditions, then the locking phase ratio differential protection.
Judgment method of the ＣＴ line-break
In order to prevent the CT relay and the protection false action,The device uses the function of setting up the time delay CT line-break alarm and the instantaneous CT line-break lock protection
1)delayed CT line-break alarm：When any phase of the difference of time is greater than 0.15Ie the another 10 seconds, the CT signal is sent out alarm,But not locked differential protection.This is also the AC sampling circuit self-test function of the 9695 transformer differential protection relay
2) Instantaneous CT line-break alarm:In the process of fault measurement，Meet any of the conditions then it does not carry out the CT line-break：The maximum phase current is less than 0.2Ie; After starting the maximum phase current is greater than 1.2Ie.
3) A side current simultaneously meets the following conditions will be considered to be CT line-break：Only one phase current is zero; the other phase currents are equal to the starting current.
- why is the price of the Generator protection unit so expensive
- The photovoltaic power will become the main battleground in the elec
- Will the intelligent power station replace the conventional power st
- analysis the future development trend of the relay protection
- The importance of relay protection in electric power system
- Application of relay protection in life
- Automatic synchronization device function,classification
- The principle and effect of the auto reclosure
- The difference between over current protection and over load protect
- What are the function of the main transformer protection?
- Function and configuration principle of the motor protection
- Overcurrent protection principle
- Principle of current instantaneous trip protection