986 busbar differential protection relay
986 busbar differential protection device using the whole panel, back-insert type chassis,Strong and weak electricity completely separated,Multilayer printed circuit board technology, strong anti-interference ability,the device has friendly man-machine interface, large screen liquid crystal display which can display a wiring diagram in real-time and the operation status of the device and protection action information.
Busbar differential protection
busbar connected dead zone protection
busbar failure protection
Busbar charge protection
busbar over current protection
Line failure protection
Using the total current differential criterion with ratio braking characteristic to achieve fast busbar differential protection.
Strong anti-TA saturability：When the system is in the area of fault, the protection then rapidly exit,Unaffected by TA saturation,TA saturation out of the area is fault, the protection is reliable and non maloperation.
When the system has the cascading failures or the failure become serious,the device also can protect .
Automatic tracking, identification of dual bus operating mode.
In order to prevent the internal fault of the main transformer, the composite voltage element may not start,Which leads to the failure of the line protection,The corresponding lines can be set to the main variable branch by switching the control words,The circuit failure protection is not protected by the compound voltage lockout.
For all kinds of the running state of the system, we can ensure the reliable and safe operation of the bus, In the conditions of double bus (single bus section) operation mode, such as a section of PT maintenance can use the 986 bus differential protection device of the open contact point PT2, PT1 will exit the operation of the PT voltage cut to the intact PT No special requirements on the main characteristics of TA. The main TA ratio is inconsistent, the user can set the settlement on the spot
Chinese LCD display, menu operation, you can conveniently view the unbalanced current running state
To configure the Chinese printer, to facilitate the printing of fixed value reports, sampling reports, self inspection reports and failure reports.
Self inspection report and trouble report.（Matching）
The front of the cabinet is provided with a main wiring diagram of the simulation system, and the operation mode is clear at a glance.
The whole panel, the back plug-in chassis structure type, strong and weak electricity completely separated
Multilayer printed circuit board technology, strong anti-interference ability.
Debugging is simple, maintenance is convenient
Ethernet communication,Optical fiber communication.
- why is the price of the Generator protection unit so expensive
- The photovoltaic power will become the main battleground in the elec
- Will the intelligent power station replace the conventional power st
- analysis the future development trend of the relay protection
- The importance of relay protection in electric power system
- Application of relay protection in life
- principle Of back-up protection
- Principle of current instantaneous trip protection
- Function and configuration principle of the motor protection
- Principle of inverse power protection of generator
- The principle and effect of the auto reclosure
- features of transformer differential protection
- Overcurrent protection principle